Water or Flexible Gas Pipe Clamps
ERITECH® brand of CWP grounding clamps are listed for connecting HEX Fittings on CSST systems.
ERICO® has developed a range of CWP Grounding Clamps which help minimize the possibility of damage from a lightning strike or other transient voltage by reducing the electrical potential between metallic objects and building systems.
The clamps, which are part of the ERITECH® line of Facility Electrical Protection products, conform to the requirements of the 2009 edition of NFPA® 54, NFGC® (National Fuel Gas Code) and NEC® (National Electric Code) for bonding corrugated stainless steel tubing (CSST) gas piping systems to the grounding conductor of the building’s electrical system.
CWP Grounding Clamps are ideal for connecting brass hex fittings on flexible gas piping, copper grounding conductors, galvanized water pipes, copper water tubing or ground rods ranging from 1/2” to 4” to a ground conductor to bond all ground points together. This helps eliminate ground loops and creates an equipotential plane.
Made of a high-strength silicone bronze, the clamps are ideal for use in applications, such as lightning protection, fault current ground, signal reference grid and static ground. They are UL® Listed (ANSI®/UL 467 Category KDER).
- Ideal for connecting copper conductors to metallic water pipe (including copper tubing or ground rods)
- Bond corrugated stainless steel tubing (CSST) or flexible gas pipe systems to the electrical system in accordance with the NFGC (National Fuel Gas Code) and the NEC (National Electric Code)
- Applications include lightning protection, fault current ground, signal reference grid and static ground
- CWP series of clamps fits hex fittings, copper grounding conductors, galvanized water pipes, copper water tubing or copper ground rods ranging from 1/2” to 4”
- UL® Listed (ANSI®/UL 467 – Category KDER)
- High-strength silicone bronze clamps connect brass hex fittings
CWP Grounding Clamps help minimize the possibility of damage from a lightning strike or other transient voltage by reducing the electrical potential between metallic objects and building systems.
|Flexibile Gas Pipe Brass Hex Fitting to Bonding Sizing|
||Flexible Tubing Size
||Hex Nut Size|
||Hex Nut Size
|Hex Nut Size|
|| 1/2 in - 1 in
||10 Sol - 2 Sol
||1 1/4 in|
||1 1/4 in - 2 in
||10 Sol - 2 Str
||1 1/2 in
||2 1/8 in|
||2 1/2 in - 4 in
||10 Sol - 4 Str
||2 1/2 in
||3 1/8 in |
UL is a registered trademark of Underwriters Laboratories, Inc.
NFPA is a registered trademark of the National Fire Protection Association.
NEC is a registered trademark of, and National Electrical Code (NEC) standard is a copyright of the National Fire Protection Association.
NFGC is a registered trademark of, and National Fuel Gas Code (NFGC) standard is a copyright of the National Fire Protection Association
ANSI is a registered trademark of the American National Standards Institute.
Warning, Warranty and Limitation of Liability
ERICO products shall be installed and used only as indicated in ERICO's product instruction sheets and
training materials. Instruction sheets are available at www.erico.com and from your ERICO customer service
representative. Improper installation, misuse, misapplication or other failure to completely follow ERICO's
instructions and warnings may cause product malfunction, property damage, serious bodily injury and death.
ERICO products are warranted to be free from defects in material and workmanship at the time of shipment.
NO OTHER WARRANTY, WHETHER EXPRESS OR IMPLIED (INCLUDING ANY WARRANTY OF MERCHANTABILITY OR FITNESS FOR A
PARTICULAR PURPOSE), SHALL EXIST IN CONNECTION WITH THE SALE OR USE OF ANY ERICO PRODUCTS. Claims for errors,
shortages, defects or nonconformities ascertainable upon inspection must be made in writing within 5 days
after Buyer's receipt of products. All other claims must be made in writing to ERICO within 6 months from the
date of shipment or transport. Products claimed to be nonconforming or defective must, upon ERICO's prior
written approval in accordance with its standard terms and procedures governing returns, promptly be returned
to ERICO for inspection. Claims not made as provided above and within the applicable time period will be
barred. ERICO shall in no event be responsible if the products have not been stored or used in accordance
with its specifications and recommended procedures. ERICO will, at its option, either repair or replace
nonconforming or defective products for which it is responsible or return the purchase price to the Buyer.
THE FOREGOING STATES BUYER'S EXCLUSIVE REMEDY FOR ANY BREACH OF ERICO WARRANTY AND FOR ANY CLAIM, WHETHER
SOUNDING IN CONTRACT, TORT OR NEGLIGENCE, FOR LOSS OR INJURY CAUSED BY THE SALE OR USE OF ANY PRODUCT.
LIMITATION OF LIABILITY
ERICO excludes all liability except such liability that is directly attributable to the willful or gross
negligence of ERICO's employees. Should ERICO be held liable its liability shall in no event exceed the
total purchase price under the contract. ERICO SHALL IN NO EVENT BE RESPONSIBLE FOR ANY LOSS OF BUSINESS OR
PROFITS, DOWNTIME OR DELAY, LABOR, REPAIR OR MATERIAL COSTS OR ANY SIMILAR OR DISSIMILAR CONSEQUENTIAL LOSS
OR DAMAGE INCURRED BY BUYER.
Due to a policy of continued product development, specifications are subject to change without notice.
CADDY, CADWELD, CRITEC, ERICO, ERIFLEX, ERITECH, and LENTON are registered trademarks of ERICO